Located in the powerhouse are two five-blade Kaplan turbines with vertical shaft. Their nominal output is 16,677 kW each. They are coupled with two 20,000 kVA three-phase synchronous generators. The ring cooling installed in the generators blows the warm air through nine externally arranged upright windows. In winter, the hot air produced by the generators can be used to heat the machine hall.Transformers:
The main transformers T1 and T2 have a nominal output of 20,000 kVA and a nominal voltage of 6.3/120 kV.Weir system:
Each weir field has a double hook gate comprising a base gate and a top gate, and is powered by two chain winches. Seven weir dam beams are provided to close each weir opening on the upstream side.