Turbines and generators:
Two horizontally installed Kaplan bulb turbines have an output of 8,250 kW each with an expansion head of 10.0 metres. The four-blade impellers with a diameter of 3.6 m have an intake capacity of 106 m³/sec. The two bulb turbine generators have a nominal output of 9,500 kVA. The generators are cooled by means of a closed circuit.
Two 9,500 kVA machine transformers raise the generated energy to 30 kV. Transmission is via a 30 kV cable lines to the Pongau substation of Salzburg AG. The plant additionally has two 400 kVA transformers to cover its own requirements. They connect the 30 kV with the 0.4 kV voltage level.
In order to control the three-field weir system, welded pressure segments in the box design with weir flaps are used. With a clear width of 10 metres, the barriers enable a total dammed height of 10.3 metres.